N 210.11(C)(4) Garage Branch Circuits. In addition to the number of branch circuits required by other parts of this section, at least one 120-volt, 20-ampere branch circuit shall be installed to supply receptacle outlets in attached garages and in detached garages with electric power. This circuit shall have no other outlets.Are you saying a code change? Which one?
Exception: This circuit shall be permitted to supply readily accessible outdoor receptacle outlets.
A garage has a lighting requirement too. OK, so it's MWBC (2 circuits), not an additional feed. My mistake in wording. And I didn't see "fast food restaurant."
I wonder, I edited something and it didn't show 'edited'.