The remodel I am working on has a customer owned meter pole containing the meter socket/200 amp service disconnect breaker. The house panel is 50' away and is fed overhead with 3 wire triplex. There is no ground rods or neutral to ground bond at the service disconnect. The neutral to ground bond was done at the house panel. If the neutral was bonded to ground at the meter socket/service disconnect as required per code would I also have to run the water pipe bonding all the way over to customer owned meter pole? Approximately 50' away across a driveway from the main house panel.