Two questions regarding this FWP-2-5( deaerator for boiler).
- Panel schedule calls for it to be fed with 3#12’s but they are using a 3P/60A disconnect switch. Disconnect switch incorrectly sized IMO.
- Mechanical schedule calls for the equipment to come with DOL starter furnished by mechanical. Some starters can me a combo starter/disconnect. Do you think the disconnect shown on the electrical is a separate loose disco or the disco is part of the starter? Or could the starter just have overloads and still have a separate disconnect provided by electrical?