Were they complaining about the length or the path? Sounds like the length because you asked, but....? Unless they don't like the almost-trivial difference in the white, it looks fine to me. (How long are those feeders, overall?)I was told to change how I ran my wire for parralel runs of feeders.
Question - is this the supply or is it the feed through lugs with service disconnect (or first disconnect of SDS) at the top end?I was told to change how I ran my wire for parralel runs of feeders. What's the code requirement for running parralel runs for feeders does the length need to match within 3%?
Sent from my Moto Z (2) using Tapatalk
Don't laugh. That's exactly the way my old boss did it and made us do it.Never heard of a percentage, just need to be reasonably close, all must take the same path, an example would be, two in the slab, one overhead would not be compliant. I know one contractor cut all pieces the exact same length, and wadded up the excess 500 mcm in the bottom of the switchgear! LOL!
No problem, take bottom panel off the cabinet - it is attached with screws. If they didn't remove the ones in the back wall before mounting it gets more difficult.I really wanna see someone take the cover off the LB under the panel.
No, not the big LB (actually, the LL)... the little one behind the connector...........