I do not think any of us think otherwise as far as Equipment Grounding Conductor the dispute is about Grounding Electrode Conductors.Originally posted by gwz2:
mike's loop of Sections seem very convincing that Grounding conductors should be green if not bare.
Please cite a code setion in the 2002 code that reserves green for grounding conductors only. The words that did this in the '99 code do not appear in the '02 code.I believe that green is reserved for grounding conductors whether they be equipment or electrode grounding conductors.
agree, agree, agree!!!!!!!!Why can't they write the code to use good English?
Should not the code "writers" have to read this forum